Website: The Green Grid
In "Recommendations for Measuring and Reporting Overall Data Center Efficiency," IT industry coalition The Green Grid lays out the details of a new, more detailed version of the Green Grid's Power Usage Effectiveness ratio for measuring data center energy efficiency.
From the introduction and background for the white paper:
The purpose of this document is to provide recommendations on measuring and publishing values for PUE at dedicated data center facilities. These recommendations represent the collective work of a task force representing 7x24 Exchange, ASHRAE, The Green Grid, Silicon Valley Leadership Group, U.S. Department of Energy Save Energy Now Program, U.S. Environmental Protection Agency’s ENERGY STAR Program, United States Green Building Council, and Uptime Institute. The recommendations are prepared in accordance with the guiding principles, presented in the following section. The task force continues to work towards a Version 2 document, which will provide corresponding guidance for mixed-use buildings.
Background – Guiding Principles for Data Center Efficiency Metrics
As business demands and energy costs for data centers rise, owners and operators have focused on the energy efficiency of the data center as a whole, frequently using energy efficiency metrics. However, the metrics are not always applied clearly and consistently. To address these inconsistencies, a group of leaders from across the industry met on January 13, 2010 to agree on data center energy efficiency measurements, metrics, and reporting conventions. Organizations represented included the 7x24 Exchange, ASHRAE, The Green Grid, Silicon Valley Leadership Group, U.S. Department of Energy Save Energy Now and Federal Energy Management Programs, U.S. Environmental Protection Agency’s ENERGY STAR Program, U.S. Green Building Council, and Uptime Institute.
The following guiding principles were agreed to:• Power Usage Effectiveness (PUE) using source energy consumption is the preferred energy efficiency metric for data centers. PUE is a measurement of the total energy of the data center divided by the IT energy consumption.
• When calculating PUE, IT energy consumption should, at a minimum, be measured at the output of the uninterruptible power supply (UPS). However, the industry should progressively improve measurement capabilities over time so that measurement of IT energy consumption directly at the IT load (i.e. servers) becomes the common practice.
• For a dedicated data center, the total energy in the PUE equation will include all energy sources at the point of utility handoff to the data center owner or operator.
For a data center in a mixed-use building, the total energy will be all energy required to operate the data center, similar to a dedicated data center, and should include cooling, lighting, and support infrastructure for the data center operations. This guidance is meant to help the industry have a common understanding of energy efficiency metrics that can generate dialogue to improve data center efficiencies and reduce energy consumption. Member organizations are committed to applying and promoting these guidelines to their programs.